Instruction/ maintenance manual of the product COI 2180206H HP
Go to page of 36
Installation and operating instructions Combi HP Thermostatic mixer shower T00219 2180206H March 2007 I nstallers please note these InstructIons are t o b e left w.
Combi HP ther mostatic mixer shower Introduction 1 Safety warnings 1 Main components 2 Siting requirements 3 T ypical suitable installations 4 Preparing the mixer valve 6 Siting of the shower 6 Fitting the shower to the wall - Exposed 7 Rising and falling supplies 7 Rear entry supplies 1 0 Fitting the shower to the wall - Built-in 1 3 Solid wall 1 3 Hollow wall 1 6 Shower cubicle or panel 1 8 Flushing procedure 2 0 Fitting the tamperproof fixed head - Exposed 2 1 Fitting the tamperproof fixed head - Built-in 2 2 Fitting the fixed head - Built-in 2 3 Fitting the bulkhead 2 4 Operating the shower 2 5 Adjusting the maximum temperature stop 2 6 Spare parts 2 7 Fault finding 2 9 Guarantee, service policy , etc.
1 Combi HP ther mostatic mixer shower INTRODUCTION SAFETY W ARNINGS C-006-A INTRODUCTION T his book contains all the necessary ﬁtting and operating instructions for your T riton high pressure thermostatic mixer shower . Please read them carefully .
2 Combi HP ther mostatic mixer shower 1. Inlet nuts and olives 2. Inlet elbows 3. V alve housing 4. Outlet adaptor 5. Outlet nut and olive 6. Outlet blanking plug 7. Cartridge assembly 8. Flow knob 9. T emperature knob 10.
3 Combi HP ther mostatic mixer shower SITING REQUIREMENTS D-003-A SITE REQUIREMENTS The installation must be in accordance with W ater Regulations/Bylaws. Minimum running water pressure: 1 bar . Maximum running water pressure: 5 bar . Maximum static water pressure: 10 bar .
4 Combi HP ther mostatic mixer shower a) Instantaneous gas-heated showers, e.g. combination boilers (fig.2) The shower control MUST be installed with a multipoint gas water heater or combination boiler of a fully modulating design (i.
5 Combi HP ther mostatic mixer shower packages with a cold take off after the pressure reducing valve to the cylinder . The layout and sizing of pipework must be such that nominally equal inlet supply pressures are achieved and the effects of other draw-offs are minimised.
6 Combi HP ther mostatic mixer shower Height of showerhead and shower to suit user ’s requirement. Shower can be mounted either side of the riser rail T00225 Before starting the installation, make sure all the openings on the valve are carefully covered to prevent ingress of any debris etc.
7 Combi HP ther mostatic mixer shower Exposed Note: The outlet of the shower must not be connected to anything other than the hose and showerhead supplied. DO NOT use jointing compounds on any pipe fittings for the installation.
8 Combi HP ther mostatic mixer shower T00022 Hose end (flat) Pipe end (chamfered) screws are slack allowing the inlet elbows to rotate to the correct position and move freely in and out of the valve housing (fig.8) . Place the valve housing centrally between the two pipes, and mark the two diagonal fixing holes (figs.
9 Combi HP ther mostatic mixer shower If installing a riser rail, fit the outlet adaptor into the bottom outlet hole in the valve housing. The adaptor is sealed with an ‘O’ ring. Make sure the adapter is fitted with the pipe end in the valve housing (fig.
10 Combi HP ther mostatic mixer shower Rear entr y supplies Note: The final separation between pipe centres needs to be about 153 mm but absolute accuracy is not essential as the inlet elbows are adjustable between 146 mm and 160 mm (fig.
11 Combi HP ther mostatic mixer shower Remove the valve. Drill and plug the holes using the wall plugs supplied. Using two hexagonal nuts (supplied), refit the valve to the pipework. Make sure the hot inlet port (marked with the letter ‘H’ on the valve housing) is connected to the hot pipework which must be on the left.
12 Combi HP ther mostatic mixer shower where it is required i.e. bottom outlet for fixed head, top outlet for a hose (fig.20) . Fit the inlet blanking trims on the underside of the cover (fig.28) . Fit the outlet trim over the outlet adaptor and slide the cover on (fig.
13 Combi HP ther mostatic mixer shower FITTING THE SHOWER TO THE WALL - BUIL T -IN FITTING THE SHOWER TO THE W ALL Opening needs to be at the bottom if using a bulkhead 200 m m 10 - 12.5 m m 48 m m 50 mm 35 m m 77.5 m m 65 mm 220 mm T00249 Fig.
14 Combi HP ther mostatic mixer shower T00251 T00253 Seal tight up to shroud T00252 Fig.31 Fig.32 Fig.33 shower from the top (falling), the bottom (rising) or the rear . Mark the route of the incoming and outgoing pipework.
15 Combi HP ther mostatic mixer shower Where this is not possible refer to the ‘flushing procedure’ on page 20. Refit the valve to the mounting bracket/wall surface and pipework (fig.32) . Tighten the inlet nuts and inlet elbow grub screws.
16 Combi HP ther mostatic mixer shower Fit the flush mount cover (fig.37) . Locate the lugs on the trim ring in the holes on the cover (fig.38) and twist clockwise. Complete the fitting of your shower accessories.
17 Combi HP ther mostatic mixer shower washer . Make sure the inlet elbows are positioned the correct way . Offer the valve up to the mounting bracket and secure using the screws provided (fig.42) . Complete the pipework to the shower marking off the length to enter the elbows.
18 Combi HP ther mostatic mixer shower T00253 Seal tight up to shroud drill and plug the holes. Note: If fitting to plasterboard, use suitable cavity fixings. Break off the alignment tabs on the flush mount plate (fig.36).
19 Combi HP ther mostatic mixer shower correct way . Offer the valve up to the mounting bracket and secure using the screws provided. Secure the mounting bracket together with the valve to the panel using two bolts in the innermost fixing holes (fig.
20 Combi HP ther mostatic mixer shower Removal and/or fitting of check valves for maintenance IMPORT ANT : It is preferable to flush the pipework before installing the valve. Where this is not possible, the procedure using a flushing cartridge should be followed.
21 Combi HP ther mostatic mixer shower FITTING THE T AMPERPROOF FIXED HEAD - EXPOSED FITTING THE T AMPERPROOF FIXED HEAD (Exposed option only) Complete the outlet pipework from the valve and cut the pipe to required length.
22 Combi HP ther mostatic mixer shower FITTING THE T AMPERPROOF FIXED HEAD - BUIL T -IN FITTING THE T AMPERPROOF FIXED HEAD (Built in option only) Complete outlet pipework from the valve ending in a ½” BSP female threaded fitting (not supplied) (fig.
23 Combi HP ther mostatic mixer shower FITTING THE FIXED HEAD - BUIL T -IN FITTING THE FIXED HEAD (Built in option only) The outlet pipe should protrude from the surface of the wall between 50 mm and 65 mm (fig.65) . Mark four fixing hole positions by using the fixed arm as a template.
24 Combi HP ther mostatic mixer shower T00081 Appropriate fitting (Riser rail option only) Complete the outlet pipework ending in a ½" x 15 mm female thread fitting (fig.68) . Note: This fitting is not supplied as variations in installations needs the selection of the most suitable fitting.
25 Combi HP ther mostatic mixer shower Make sure all plumbing supplies are connected and turned on. Starting the shower T o start the shower , turn the outer knob (flow control) anti-clockwise (fig.74) . Adjusting the shower temperature T o adjust the temperature, turn the inner knob — temperature control (fig.
26 Combi HP ther mostatic mixer shower T00297 0D[LPXPWHPSHUDWXUHVWRSPHFKDQLVP 'HFUHDVHVWRSSRVLWLRQ,QFUHDVHVWRSSRVLWLRQ 7 5 , 7 2 1 7 5 , 7 2 1 *URRYHV 7 HPSHUDWXUHFRQWUROGLVF T00296 Fi xi ng sc re w T e mp era tu re co nt ro l k no b T e mp era tu re co nt ro l d is c Fig.
27 Combi HP ther mostatic mixer shower T00298 1. HP valve cartridge (built-in valve) 83304970 2. HP cartridge and brass housing (exposed valve) 83304960 3. Outlet adaptor chrome 7031462 gold 7031463 4.
28 Combi HP ther mostatic mixer shower T00299 SP ARE P ARTS 14. Bulkhead assembly white 83303780 chrome effect 83303770 gold effect 83303790 − T rim disc (use with flush gold effect) 7051451 15.
29 Combi HP ther mostatic mixer shower X-006-A T urn the control knob anti-clockwise. T urn the control anti-clockwise. Reduce the simultaneous demand from supply — make sure a dedicated supply to mixer . Contact Customer Service for advice on ﬂow regulators.
30 Combi HP ther mostatic mixer shower FAUL T FINDING Problem/Symptom Cause Action/Cure X-006-A T urn t h e contro l k no b anti-c l oc k wise. T urn the control anti-clockwise. Reduce the simultaneous demand from supply — make sure a dedicated supply to mixer .
31 Combi HP ther mostatic mixer shower .
32 Combi HP ther mostatic mixer shower .
33 Combi HP ther mostatic mixer shower .
T riton Showers T riton Road Nuneaton W arwickshire CV11 4NR T riton is a division of Norcr os Group (Holdings) Limited TRITON reserve the right to change product speciﬁcation without prior notice. E&OA. © TRITON SHOWERS 2008 Service Policy In t he e ve nt of a c om pl ai nt oc cu rr in g, t he fo ll ow in g pr oc ed ur e sh oul d be f ol lo we d: 1 T elephone Customer Service on 08 70 0 67 3 33 3 ( 08 45 7 62 6 59 1 i n Sc ot la nd an d in N or th er n Ire la nd ) , h av in g a va il ab le t he mo de l nu mb er a nd p owe r ra ti ng o f the p ro du ct , tog et he r wi th t he d at e o f pu r ch as e.
An important point after buying a device HP COI 2180206H (or even before the purchase) is to read its user manual. We should do this for several simple reasons:
If you have not bought HP COI 2180206H yet, this is a good time to familiarize yourself with the basic data on the product. First of all view first pages of the manual, you can find above. You should find there the most important technical data HP COI 2180206H - thus you can check whether the hardware meets your expectations. When delving into next pages of the user manual, HP COI 2180206H you will learn all the available features of the product, as well as information on its operation. The information that you get HP COI 2180206H will certainly help you make a decision on the purchase.
If you already are a holder of HP COI 2180206H, but have not read the manual yet, you should do it for the reasons described above. You will learn then if you properly used the available features, and whether you have not made any mistakes, which can shorten the lifetime HP COI 2180206H.
However, one of the most important roles played by the user manual is to help in solving problems with HP COI 2180206H. Almost always you will find there Troubleshooting, which are the most frequently occurring failures and malfunctions of the device HP COI 2180206H along with tips on how to solve them. Even if you fail to solve the problem, the manual will show you a further procedure – contact to the customer service center or the nearest service center